IEC. First edition. Surge arresters –. Part 6: Surge arresters containing both series and parallel gapped structures –. Rated 52 kV and less. This part of International Standard IEC applies to surge protective devices designed for repeated operation to limit voltage surges on a.c. power circuits. This part of IEC applies to non-linear metal-oxide resistor type surge arresters without spark gaps designed to limit voltage surges on a.c. power circuits.
|Published (Last):||20 August 2015|
|PDF File Size:||17.5 Mb|
|ePub File Size:||16.51 Mb|
|Price:||Free* [*Free Regsitration Required]|
Systems which permit earth faults to remain undetected or operate with one phase earthed for periods in excess of 24 hours will require the use of an arrester having a Uc continuous capability equal to the system maximum phase-to-phase voltage. After production, every MOV disk must pass a series of electrical tests designed to ensure the highest individual disk quality.
Also, such a fair allows us to understand and analyze the competition. Electricity distribution companies from more than 40 countries worldwide already made the decision to trust the knowledge and technology of our company. Power-Frequency Overvoltages The second application criterion to be met is a condition established by the effectiveness of system grounding. Full text browsing Price: This document defines surge arresters to protect the insulator assembly from lightning-caused over-voltages only.
EVS-EN IEC – Estonian Centre for Standardisation
Considering the particular design concept and the special application on overhead transmission and distribution lines, some unique requirements and tests are introduced, such as the verification test for coordination between insulator withstand and EGLA protective level, the follow current interrupting test, mechanical load tests, etc.
Gapless surge arresters must be selected with sufficient steady-state self impedance to withstand the application of line-to-earth power frequency voltages under all system conditions of operation.
IEC System of Conformity Assessment Schemes
Using Metal Oxide Varistors MOVs having excellent electrical properties, these arresters provide superior overvoltage protection for MV distribution systems.
NKI – tension insulators Our tension insulators have specified mechanical load 90 kN. In our production is already for 9 months fully implemented the collaborative robot UR5 from the Danish company Universal Robots.
NKI – tension insulators
To ensure that the arrester’s capabilities will not be exceeded, the resources of the Thomas A. Irc addition to testing to evaluate the performance of the MO resistors, procedures for evaluating the performance of the EGLA series gaps have been introduced.
UltraSIL silicone rubber will not support biological growth algae and mildew and is non-flammable.
The UltraSIL housed surge arrester incorporates the industry recognized superior polymeric material — silicone rubber. One must 60099 particular attention to systems having low coefficients of grounding, ungrounded systems and systems that are resonant grounded or that may become ungrounded under abnormal conditions of operation. Our showroom A41 was in Hall Our most important products are low and medium voltage surge arresters and medium voltage insulators.
Table 1 in Catalog Section I provides a general application guide for the selection of the proper arrester rating for a given system voltage and system grounding configuration. The Lightning discharge capability test has been completely re-written and re-named to Test to verify the repetitive charge transfer rating, Qrs with lightning discharges to reflect changes introduced in IEC Ed.
Manufacturing our own MOV disks allows strict quality control over the manufacturing process from start to finish.
Valid Estimated date of Estonian translation publication: The second application criterion to be met is a condition established by the effectiveness of system grounding. The rating of an arrester is the maximum power frequency line-to-ground voltage at which the arrester is designed to pass the IEC operating duty test. The fair also presents an opportunity to deepen existing contacts. Consult with your Cooper representative to have your individual system application needs studied.
The advantages of polymer housed arresters — reduced size and weight, and enhanced safety — have been refined in this new generation of surge arresters: A disconnector that has operated gives a visual indication of internal arrester damage and the need for arrester replacement. Edison Technical Center and their systems application engineers are available to make recommendations.
Your shopping cart is empty. This edition constitutes a technical revision. A ground lead disconnector is optionally available for use on systems having 20A or more of available fault current. The fair fulfilled our expectations.
In the public tender “Incentives for research and development projects 2” we received grants for “Development of a system for monitoring the functionality of surge arresters”. Therefore, and since metal-oxide resistors are not permanently connected to the line, the following items are not considered for this document: Metal-oxide surge arresters with external series gap EGLA for overhead transmission and distribution lines of a.
We are particularly pleased by the visit of this fair because we carried out some business talks with potential customers with whom we met at the Hanover Messe fair in previous years. These MOV disks have proven their reliability and protective abilities through oec of in-service use.
The voltage withstand capability application ied ungrounded systems is 1. The number of visitors and established business contacts is in line with expectations. Shopping Cart Your shopping cart is empty. Surge arresters – Part 8: